Past centuries are characterized by persistent growth of urban population. At present, more than half of the world’s population currently lives in cities . It is predicted that by 2050 the urban population will reach 70 % . As the major part of population live in cities, future cities must meet severe demands imposed by a sustainability concept, which includes several interrelated areas, such as, energy, ecology, economics, politics and culture [3–5]. In this review, the first domain is mainly addressed and energy efficient buildings, which are an essential constituent of future sustainable cities, are considered. In order such buildings to ensure high levels of comfort and convenience without necessarily sacrificing the standards of living, an input of emerging low-carbon technologies aimed at rational use of thermal energy in dwellings must be decidedly increased [5, 6].
Indeed, at present, a significant part of primary fossil fuels is spent for heating/cooling of buildings, thus, greatly contributing to GHG emissions. In Europe, the heat consumption in buildings (heating and hot water production, HHWP) is responsible for 24 % of the total energy consumption of the EU-27 (2008) . Forty five percent of total UK final energy consumption for 2012 was for heating purposes; it being known that more than half (24 %) was used for domestic heating . A one fourth of this amount is additionally used for domestic hot water [8, 9]. According to the Parliament Committee , residential GHG emissions account for 66 % of buildings emissions. The building sector in Canada accounts for about 30 % of total GHG emissions . In Germany, the share of households in total final energy consumption in 2011 reaches 25 % or 52 Mtoe (million tonnes of oil equivalent), space heating being dominated (72 % of the final households energy consumption ). More data for Germany together with similar information for China and the USA can be found elsewhere [13, 14]. In the Russian Federation (RF), 43 % of the produced centralized heat or 138 Mtoe is used for buildings . This agrees well with the data of ref.  that Russian residential, public, and commercial buildings in 2005 were responsible for 144.5 Mtoe of final energy use (Table 1), at that 75 % of this heat is consumed in dwellings. Space heating is the leading heat end-user (73.7 % in 2011), while the rest (26.3 %) is used for HHWP .
|Type||Consumption in 2005||Technical potential||Economic potential||Market potential, 2010 prices|
|Public and commercial||36.31||15.20||13.81||11.72|
Despite all systematic and active actions that have gone on, heat losses in buildings still remain enormous, hence, there is considerable potential for improving energy efficiency in residential buildings and the related infrastructure. According to the International Energy Agency (IEA), the building sector can reduce energy consumption with an estimated global energy savings of 1509 Mtoe which can possibly mitigate 12.6 Gt (gigatonnes) of CO2 emissions by 2050 . The UK Government has set an ambitious target to reduce national greenhouse gas emissions by at least 80 % by 2050, and about a half of this reduction is to be due to improved operation of buildings. Similarly, the declared national German policy goal is to reduce nation-wide CO2 emissions by 80 % till 2050 (against 1990). According to a recent study, about 60 % of that reduction has to come from the building sector .
Technical potential of energy saving in the Russian buildings sector exceeds 68 Mtoe or 47 % of the total consumption, the largest potential being evaluated for residential buildings (Table 1) . The major part (67 %) of saving can be implemented through the reduction of district heating use for space heating and hot water. About 85 % of the technical potential is economically viable, while 72 % is market attractive with the 2010 energy prices . Essential saving can be also reached by improving the infrastructure of centralized heat supply . Similar estimations were reported in : a technical GHG reduction potential for the Russian building stock by 2030 ranges between 26 and 47 % of the national baseline.
The UK has around 26.7 million domestic houses and flats , and this building stock is one of the oldest in Europe. Old houses have significantly higher heat consumption: e.g. a typical Victorian house demands more than twice as much energy for space heating than a modern house . Much of the heat supplied to UK buildings is wasted, that is mainly due to poor buildings insulation, heating of unoccupied spaces or inappropriate occupant behaviour . As seen from Fig. 1b, for average dwelling, the main losses due to building fabric are related to heat fluxes through the walls (37 %) and windows (19 %) together with those associated with air infiltration in ventilation system (18 %). Heating water for showers, baths and sinks demands around 87 TWh a year, and this heat is completely lost .
By the end of 2012, the total floor area of dwellings in Russia reached 3.3 billion m2, 72.2 % being related to urban development . In Russia, the space heating is responsible of 58 % of overall energy consumption in residential buildings with district heating systems which cover c.a. 75 % of all dwellings. A small part of dwellings built after 2000 meet acceptable heat efficiency requirements, whereas the majority of older buildings have significantly lower space heating efficiency. The value of Specific Energy Consumption (SEC) for space heating strongly depends on the year of dwelling construction: for buildings erected before 1990, in 1991–2000 and after 2000, the average SEC is estimated as 0.97, 0.55 and 0.38 GJ/m2/year, respectively . New, and much more severe, standards for thermal protection of buildings were set in 2003 by a new Russian building code (SNiP 23–02–2003 “Thermal Performance of Buildings” ). These standards are based on the total number of heating degree-days (HDD) for particular climatic zone/city. The heating period H is fixed as a cold season with the mean daily outdoor temperature Tind ≤ 8 °С. For Moscow, H = 214 days and HDD(Tind ≤ 8 °С) = 4,943 (°C⋅day)/year, for Novosibirsk – 230 days and 6,601 (°C⋅day)/year, and the average HDDs in Russia is 5,140 (°С⋅day)/year. For comparison, in London the HDD(Tind ≤ 10 °C) is only 1,860 (°С⋅day)/year (in 2006) [http://ukclimateprojections.metoffice.gov.uk/media.jsp?mediaid=87928&filetype=pdf]. Thus, in the RF the demand for thermal energy needed for space heating is significantly larger than in the UK.
Another important factor affecting the heating standards is the dwelling size or the number of storeys. Thermal performance of individual low-rise buildings (1–3 storeys) and multi-storied apartment buildings (4–25 storeys) differs essentially: in smaller dwellings, 1 m2 of heated rooms area is accompanied by 1.7–3.3 m2 of building fabric area, whereas for larger buildings this ratio is considerably less and varies from 0.6 to 1.3 m2 , which leads to radically lower heat losses through the building constructions (Fig. 2). It is interesting to mention that the structure of heat losses in the Russian dwellings erected before 2000 (the left half of Fig. 2) is close to that reported for the average building in the UK (Fig. 1b).
Accordingly, the current strategic tendency is a decrease in heat consumption in dwellings by reducing heat losses. The heat consumption can also be reduced by applying inter-seasonal heat storage. During the summer period there is an excess of solar heat available that meets little or no heat demand which is shifted to the winter months. The inter-seasonal adsorptive heat storage (AHS) has been considered as a tool to harmonize the heat availability and demand, and, hence, to cover/reduce heating peaks in winter period (see 3.1).
An important tendency clearly seen from Fig. 2 is that, for modern dwellings with better fabric insulation, a portion of the heat losses due to air infiltration significantly increases and becomes dominant (almost 50 %) in high-rise buildings. Therefore, a further improvement of the dwellings thermal efficiency is associated, first of all, with a decrease in heat losses due to air infiltration. This can be achieved by implementation of new technologies of indoor climate control, including emerging adsorption methods (see e.g. [24–27] and 3.2 below).
Possible directions of future R&D directed at further improving AHS technologies for dwellings are briefly considered in 3.3.
Although there are many applications of adsorption technologies for rational use of energy [29, 30, 31, 32, 33], we consider here those which focus mainly on the building sector.
Inter-seasonal heat storage can be an effective tool to reduce heating peaks in dwellings in winter period [28–34]. Indeed, solar heating potential is high in summer and low in winter, what is just opposite to heat demand (see e.g. Fig. 1 in ref. ), therefore a long-term (several months) storage of the excess heat in simmer is needed. The inter-seasonal AHS can operate as closed (evacuated)  and open (coupled to the ambient)  cycles. Useful comparison of these two AHS variations was performed in  by using energy and exergy balance analysis. The authors clearly demonstrated that the adsorptive systems may be as efficient as, and more compact than other types of the thermal energy storage systems, however, there is a much room for efficiency improvement for both closed and open AHS systems.
The density A of adsorption heat storage is considered to lie between 100 and 500 kWh/m3 or (0.36–1.8) GJ/m3 being larger than that of sensible (c.a. 50 kWh/m3) and latent (c.a. 100 kWh/m3) heat storage [29, 30, 39–41]. If the annual heating demand is 25 kWh/m2/year that is typical for standards of low energy buildings in Europe a 100 m2 house consumes for heating about 9 GJ per year. These heat needs can be, in principle, covered by solar energy, because even in the UK the amount of solar radiation incident on a correctly orientated roof of a typical house exceeds its energy consumption during a year . Accordingly, efficient inter-seasonal heat storage is necessary in this case. The volume of a heat storage material is reasonable (2–10 m3) only if the storage density is above 1 GJ/m3 (270 kWh/m3). In actual practice, the volume of the heat storage unit is larger than the material volume itself by a factor of 2–4 due to volumes of heat exchangers, evaporator/condenser, pumps/fans, pipes, etc.
For countries with colder climate, means, a larger HDD-value, like Russia, the adsorption storage alone can hardly cover the overall heat demand during winter. In this case, the heat storage systems need to work alongside a complementary space heating unit.
It is worthy to make an estimation of tentative upper limit of the AHS storage density. Water has a large heat of evaporation ΔHev, and is considered as the most promising and ecologically clean working fluid for AHS applications. For making this estimation, let’s assume that the heat storage process is simply water evaporation. During this endothermic transition of water molecules from liquid to vapour state, the amount of heat consumed (stored) is A(H2O) = ΔHev = 2.25 MJ/kg = 2.25 GJ/m3 = 630 kWh/m3 (at 100 °C). For AHS, the amount of heat needed for complete water desorption (or maximal heat storage density Amax) is
|Adsorbent||wmax, g/g||ΔHdes, MJ/kg||, MJ/kg||, GJ/m3||Reference|
|Silica gel Fuji RD||0.4||2.40||0.96||0.77|||
|SWS-1 L = CaCl2/silica gel||0.65||2.65||1.72||1.55|||
|SWS-9 V = LiNO3/Vermiculite||1.80||2.30||4.15||1.16|||
|SWS-1 V = CaCl2/Vermiculite||1.80||2.35||4.2||1.25|||
|SIM-3b = MgSO4/Vermiculite||1.94||-||0.41a||0.14|||
|(MgSO4 + MgCl2)/Attapulgite||-||-||1.59b||-|||
Eqs. (1) and (2) take into account only the latent heat of material. A useful method of experimental evaluation of both latent and sensible heat was suggested in  and then used in  and . The sensible heat was found to be 4–7 % of the latent one (in the temperature range 50–200 °C) and can be used either for immediate consumption (e.g. for HHWP) or short-term storage.
Under real conditions the storage density is expected to be lower than the maximal one calculated by eqs. (1) and (2), because only a part of the adsorbed water is involved in the storage process. To realize how much water can be involved, let’s consider a simple three temperature (3T) closed cycle of AHS unit. Although the thermodynamics is similar, an open AHS cycle is considered on a psychrometric chart of humid air (not presented) as described in . Practical implementations of the AHS open and closed systems are quite different as well (see 3.1.4).
This cycle consists of two isosters and two isobars and is commonly presented on the Clapeyron diagram ln(P) vs. (−1/T) (Fig. 3). During isobaric desorption (2–3) the amount of water adsorbed reduces from wmax to wmin, and the heat Qd consumed for the water desorption is stored. The stored heat can be release during isobaric adsorption (4–1) when the dewatered adsorbent sucks water vapour from an evaporator (for closed AHS cycles) or from the ambient air (for open cycles). The heat of evaporation Qe is deemed to be taken from the ambient for free. Between the charging (2–3) and discharging (4–1) stages the heat can be stored as long as needed without any heat insulation.
Three temperatures (those of evaporator Te, condenser Tc = T1, and external heat source Tg) uniquely define the cycle . The heat Qa is released for consumers at temperature ranging between T4 and T1 = Tc, therefore Tc should be at least 30–35 °C (the lowest input temperature for floor heating). The heat of condensation Qc can also be used for heating at temperature Tc. For simple and relatively cheap flat receivers of solar energy, the temperature of heat carrier Tg available for water desorption commonly is 70–110 °C. Hydration of adsorbent up to the maximal uptake wmax occurs at point 1 by absorbing water vapour saturated at temperature Te = 5 – 15 °C. For a model AHS cycle, we have fixed the following set of temperatures: Te = 10 °C, Tc = 35 °C, and Tg = 90 °C, and calculated the mass of water exchanged along such cycle Δw = wmax – wmin and appropriate cycle heat storage density that appears to be lower than the maximal one displayed in Table 2 by a factor of 2–12 (Table 3). Significant reduction of the storage density is especially typical for zeolites which need the regeneration temperature much higher than the set temperature Tg = 90 °C. This confirms that a high affinity of adsorbent and adsorbate to each other or/and a large total sorption capacity are not important of themselves. The heat storage density is defined by the amount of adsorbate exchanged within the particular AHS cycle, means, under certain conditions of heat storage process .
Thus, the inter-seasonal heat storage can cover whole winter heating needs for low-energy buildings in a relatively mild climate (reasonable HDD-value). For less perfect buildings and colder climates, the heat stored during summer can yet be used in winter to reduce fossil fuel consumption, smooth heating peaks and, hence, decrease bills for heating. In this case, the AHS can be used as an auxiliary tool for common space heating system.
The 3T cycle on Fig. 3 allows introducing other two parameters important for AHS:
b) a temperature lift L = (Tc-Te). A large temperature lift permits higher temperature level of heat released during heat rejection (discharging) stage. For working pairs that follow Trutoun’s rule, the temperature lift can be estimated as .
For advanced AHS performance, it is necessary to have an adsorbent with high heat storage density, large temperature lift L, and low regeneration temperature Tg. It is evident, that two last requirements are in a certain conflict. Indeed, the regeneration process is easier for adsorbents with low affinity to water vapour, whereas a large temperature lift, on the contrary, needs high affinity. Therefore, intelligent compromise between these tendencies is necessary. We do not consider here dynamic parameters of the promising adsorbents, because the overall dynamics in real AHS units is more dependent on the organization of heat and mass transfer in the overall unit “adsorber – heat exchanger”, Ad-HEx (see 3.1.4 and 3.5).
The largest overall storage density 50]. They present a family of solid sorbents specifically developed in the Boreskov Institute of Catalysis (Novosibirsk, Russia) for adsorptive transformation and storage of low temperature heat [50, 51]. The SWSs were shown to exhibit an intermediate behaviour between solid adsorbents, salts hydrates and liquid absorbents. Combination of high storage density of the salts and good mass transfer of the porous matrix allows the design of advanced materials and AHS units with high efficiency and specific power. Very important advantage of SWSs is an opportunity for nano-tailoring their sorption properties by varying the salt chemical nature and content, porous structure of the host matrix and synthesis conditions [51, 52]. It is especially valuable for inter-seasonal AHS, because allows adaptation of a heat storing adsorbent to particular climatic conditions at the location of AHS unit. At present, these materials are comprehensively tested in many laboratories all over the world [28, 29, 35, 53].(up to 1.55 GJ/m3) was documented for composites “salt in porous matrix” that are known as Selective Water Sorbents (SWSs) [
Loose grains of clay mineral attapulgite impregnated with mixture of MgSO4 and MgCl2 hydrates was investigated for suitability as a heat storage material . It was shown that the partial substitution of MgSO4 by MgCl2 resulted in higher sorption heat. This larger heat release was accompanied with higher temperature lift. The energy density of the composite containing a mixture of 20 wt.% MgSO4 and 80 wt.% MgCl2 and saturated at Ta = 30 °C and RH = 85 % was 1590 kJ/kg. The desorption temperature of 130 °C was sufficient for the composite regeneration, that makes the new material promising for solar thermal energy storage.
Systematic study of the SWS-type composites for AHS was performed in refs. [35, 55]. The authors tested various hygroscopic salts (CaCl2, MgSO4, Ca(NO3)2, LiNO3, and LiBr) and host matrices (silica gel, zeolite, activated carbon and mineral vermiculite) to obtain their combinations promising for open AHS systems and studied them by a variety of physico-chemical methods (BET, BJH, TG, DSC, SEM, EDX, etc). It was found that the sorption capacity of all composite materials is significantly higher (up to 1.9 g/g) compared to their raw host matrices alone suggesting the addition of the salt is beneficial for moisture and, hence, heat storage. It was demonstrated that the pore structure damage may occur for the non-vermiculite matrices, however no damage was observed in the vermiculite as a host. Vermiculite with either lithium bromide or calcium chloride appears to have significantly larger AHS potential when compared to both the raw matrices and the other composites .
A recent survey of the current-state-of-the art of the SWS materials can be found elsewhere . In particular, the authors considered potential troubles that could impede an actual reduction of these new composites to practice. This is, first of all, a leakage of the salt solution formed during sorption out of the matrix pores, which can cause a corrosion of metal parts of AHT unit and emission of non-condensable gas. Several ways to avoid, or at least lessen, this shortcoming were considered in .
Quite interesting storage parameters were obtained for new zeolite-like materials that do not contain silicon, namely, pure and substituted aluminophosphates [56–59]. E.g. an APO-Tric material was suggested for use in low temperature solar energy storage , because it exchanges 0.25 g H2O/g in an extremely narrow range of the relative pressure P/Po = 0.12–0.15 and can be regenerated at 80–90 °C. Quite promising storage properties were revealed for SAPO-34, AlPO-18, AlPO-17, AlPO-5, etc . The disadvantages of this class of materials are a relatively small pore volume (e.g. 0.33 cm3/g for AQSOA-Z02, Table 2) and high cost. The main practical strength is an availability of several commercial adsorbents (AQSOA-Z01, AQSOA-Z02 and AQSOA-Z05) in the form of coated heat exchangers produced by the Mitsubishi Plastics Ltd. (see refs. [59–61] and Fig. 4d).
Among new AHS adsorbents, metal organic frameworks (MOFs) are attracting an increasing attention (e.g. MIL-101, MIL-125NH2 and MOF-841 in Table 2) due to their unique combination of properties such as high surface area, crystalline open structure, tunable pore size and functionality [62–64]. These materials can exhibit very large water adsorption capacity (e.g. 1.4 g/g for MIL-101, Table 2) and low regeneration temperature, however, their affinity to water is, in general, too low to ensure sufficient temperature lift. In our opinion, the potential of MOFs for AHS has not been unveiled yet, and it is quite possible that a target-oriented modification or screening of MOFs will reveal novel working pairs highly efficient for AHS. In particular, very promising results have been reported for UiO-66NH2 , MIL-125NH2 , MOF-801 and MOF-841 .
The above analysis is mainly based on considering the storage density, temperature lift and regeneration temperature, and do not take into account other important practical requirements to adsorbent optimal for AHS. These are minimal or no adsorption/desorption hysteresis, low costs and easy availability, high cyclic stability, free from poison, non-combustibility, no environmental effects, low maintenance requirements, etc. Some of these issues have become clear during practical testing of the advanced adsorbents as reported below.
Since a large variety of adsorbents have already been tested for AHS, we consider here only several selected, mostly recent, examples of both open and closed AHS systems, and refer a Reader to appropriate review papers (e.g. [28–40, 68–70]) and references therein.
Among open AHS systems the most famous and well tested is an open heat storage system installed in a school building in Munich (Germany) and connected to the local district heating network . It contained 7,000 kg of zeolite 13X as beads. The unit was tested during the heating period 1997/98 under the following conditions: the air flow rate−6,000 m3/h, the desorption temperature−130 °C, the pressure of water vapour at the heat release stage−32 mbar that corresponds to a dew-point of 25 °C. For a large temperature lift of 40 °C, a maximal energy density is estimated to be 0.49 GJ/m3 (or 0.55 GJ/m3 if the sensible heat can be utilized), whereas in the experiments a lower value of 0.446 GJ/m3 was recorded, which is 81 % of the theoretical one. Such a large storage density is due to a relatively high regeneration temperature of 130 °C. It is worthy to remind that for the above model AHS cycle with lower regeneration temperature of 90 °C, (Table 3).
The authors of  analysed the performance of several candidate materials (1.5 dm3 of adsorbent) under experimental hygrothermal cycling tests together with energy and exergy analysis of the results obtained. They tested eight composites “salt in porous matrix” identified before in  as well as raw zeolite 13X and mesoporous silica gel (Geejay Chemicals, UK) under typical conditions of open AHS cycle. The studied adsorbents were located in a test tray as a bed of loose grains. It was found that the zeolite provided the highest temperature lift, however, after the initial period (1–2 h), the moisture adsorption rate and thus heat generation decreased sharply. A sharp drop in performance over the four cycles was found for zeolite 13X which requires a higher regeneration temperature (>180 °C) than that used (100 °C) for the research. The composite SIM-3a (vermiculite doped with CaCl2) was found to be the most promising candidate for open TES systems due to its larger heat generated (120–160 kWh/m3) and rapid mass uptake at higher RH levels. Moreover, SIM-3a is non-toxic material, has a low regeneration temperature, good cyclic ability, and low cost (~0.48 $/kg) . It is worthy to note that for inter-seasonal heat storage the material cost is far more important than for short-term heat storage.
The authors of ref.  used as a host porous matrix another cheap mineral material, that was a Wakkanai siliceous shale (WSS). The WSS is a type of siliceous mudstone that is widely distributed in Wakkanai, the northern part of Hokkaido (Japan). It is a natural mesoporous material composed of silicon dioxide (SiO2) with pores of 5–40 nm size. A new AHS composite was formed by inserting LiCl into the WSS pores. To overcome the problems of low heat and mass transfer and high hydrodynamic resistance in an open AHS system, the WSS was formed by adding a binder into a honeycomb ceramic element of 10 cm x 10 cm x 20 cm with 36 cells/cm2 and a cell wall thickness of 0.28 mm (Fig. 4a). The composite containing 9.6 wt.% LiCl showed a good potential for storing heat with a volumetric heat storage density of 0.180 GJ/m3 and could supply air heated up to 53 °C. No material degradation was observed during at least 250 cycles at a quite low desorption temperature of 60 °C.
An open-type AHS setup equipped with 40 kg of composite sorbent CaCl2/(mesoporous silica gel) was tested as a batch adsorber in [72, 73]. The concentration of the CaCl2 impregnating solution was found to be an important factor affecting the storage properties of the composites. The composite prepared by impregnating silica gel with a 30 wt.% CaCl2 solution showed a high storage capacity of 1.02 MJ/kg (0.81 GJ/m3) that remained stable after 500 consequent sorption/desorption cycles. The heat discharging temperature varied from 47 °C to 30 °C and the sorbent can be charged at temperature 90 °C or below. Mathematical modelling of the AHS process predicted that the specific heat storage capacity can be increased up to 1.35 MJ/kg at a regeneration temperature of 100 °C .
SWS-type materials were successfully used also in closed AHS systems . For instance, lithium nitrate was introduced into silica gel  and vermiculite  matrices and tested in typical AHS cycle (Fig. 5). LiNO3 is a salt which bounds water less strongly than calcium chloride, lithium bromide or calcium nitrate already reported for AHS applications. Therefore, this composite sorbent was specifically developed to operate at low regeneration temperature (<65–70 °C). The sorbent particles were embedded inside a compact heat exchanger of a finned flat-tube type (Fig. 4b, c). This Ad-HEx configuration has the following advantages: a) compactness and low weight, as the heat exchanger is made of aluminium; b) good heat transfer properties due to the high heat transfer area and a high thermal conductivity of aluminium; c) high vapour permeability as provided by granular packing. Fig. 4b, c shows the overall and the detailed view of the Ad-HEx with loose silica gel grains. The distance between the fins was about 2 mm, so that 2–4 grains could be housed in this gap.
The composite LiNO3/vermiculite (SWS-9 V) exchanges 0.43 (g H2O)/(g sorbent) in an exceptionally narrow temperature range, 33–36 °C (heat rejection) and 62–65 °C (adsorbent regeneration), corresponding to a remarkable heat storage capacity of 1.15 MJ/kg. It is much larger than for similar composite based on mesoporous silica gel, SWS-9 L (Fig. 5). If relate the storage capacity to the total volume of the Ad-HEx unit (Fig. 4b), it is equal to 0.45 GJ/m3. This is superior to common adsorbents and Ad-HEx units suggested for storage of heat with temperature potential of 60–70 °C.
Another solution for enhancing heat and mass transfer was investigated for the residential application in . A commercial heat exchanger was adopted for an adsorption bed to quicken the charging process by improving heat and mass transfer. It is a copper tube and aluminium plain fin type heat exchanger with 12 parallel four-pass circuits, 1.8 mm fin spacing and a 0.25 mm thickness adsorbent coating on all fin and tube surfaces (Fig. 4d). The commercial material AQSOA-Z01 (Mitsubishi Plastics)  was used as the adsorbent bed material. When the regeneration and heat rejection temperatures were 70 °C and 30 °C, respectively, the heat storage density was found to be 0.805 MJ/kg or 0.15 GJ/(m3 of the Ad-HEx). The loading difference was 0.164 kg water/kg adsorbent. The authors suggested several possible solutions for the system performance improvement, e.g. adding more adsorbents into the fin spacing of the Ad-HEx or onto heat transfer tubes to form consolidated layer.
This brief overview of the current practice in inter-seasonal AHS shows that
To summarize, despite the significant progress in adsorbent synthesis and applications in various AHS cycles, still there is a big room for their further optimization and development of new adsorbents with advanced and pre-requested properties.
As manifested above, an efficient way of further improvement of the dwellings thermal efficiency is associated with heat recovery from the ventilation systems. This is especially important for countries with a cold climate (typical of Russia, Canada, the North Europe and USA), where the difference between indoor and outdoor temperatures can reach in winter up to 60 °C or even more. This leads to enormous heat losses, therefore efficient exchange of heat between the exhaust and supply air fluxes is absolutely necessary for reducing the heat losses. Numerous experimental and modelling studies have clearly demonstrated that up to a 90 % heat recovery can be reached by using modern plate [78, 79] and regenerative [80, 81] air-to-air heat exchangers. Another problem that appears during cold winter is continuous loosing of moisture through ventilation system [82, 83]. Indeed, the absolute humidity of supplied (outdoor) air is extremely low (e.g. ≤ 0.29 g/m3 at -30 °C), that results in dramatic reducing the indoor relative humidity (down to 10–20 % or even below) in winter season that greatly disbalances the indoor thermal comfort. Therefore, in cold countries it is extremely important to organize not only heat exchange, but moisture exchange between the fluxes as well to maintain the indoor humidity within the reasonable range. One of the solution is the application of porous and polymer membranes partially permeable for moisture as suggested in [83–85]. A new approach (the so called VENTIREG) was suggested in  for simultaneous regeneration of both heat and moisture in ventilation systems for cold climate countries. This approach was deemed to ensure an efficient moisturizing of the supplied air to approach indoor conditions of human thermal comfort which is extremely important because people spend more than 90 % of their time in buildings .
The main principal of the VENTIREG method is as follows (Fig. 6a). To exchange the sensible heat between the inlet (fresh) and outlet (exhausted) air fluxes, a granulated layer (1) of heat storing material is placed closer to the unit exit. Before this layer, layer 2 of water adsorbing material is located closer to the room side. It serves as a water buffer. The unit operates in two modes:
To study and optimize the heat and moisture recovery, four experimental units with the air flux up to 25 (I), 40 (II) and 135 (III and IV) m3/h were built and tested. Both common (silica, alumina) and novel (SWS-1A = alumina impregnated with CaCl2) adsorbents were used as buffers of water. The composite sorbent SWS-1A was found to demonstrate better performance than the common commercial adsorbents. Owing to higher adsorption capacity of this composite, the adsorbent loading is less by a factor of 2–3 that leads to smaller unit size and much lower hydrodynamic resistance of the unit. This could allow the using of cheap blade-type fans instead of centrifugal ones and give a reduction of the electricity consumption. Units III and IV consume for air blowing 20–40 W of electric power and give the heating load of about 600–1400 W that corresponds to a Coefficient of Performance of 25–35. So little electricity consumption is a very important advantage of the VENTIREG approach. Prototype IV (Fig. 6b) was constructed in a way to ensure a continuous operation, not intermittent as for units I-III .
Thus, the tested VENTIREG units exchange stale, contaminated room air with fresh outdoor air, recovering up to 95 % of heat and 70–90 % of moisture from the exhaust air. Moreover, it prevents the formation of ice at the unit exit that is one more severe problem to be solved under real winter conditions . According to the data of Table 3 of the recent review paper , the VENTIREG unit demonstrates the best properties among different heat and mass recovery systems tested under various cold climate conditions.
Despite a significant progress in AHS achieved, still there is a much room for further developing this emerging technology [48, 88, 89]. To reach this ambitious goal, systematic R&D must be made at least, but not last, in the following directions:
In this paper we consider the role of adsorption-based technologies for more rational use of heat and better thermal comfort in buildings. Based on the structure of typical heat losses in modern dwellings, two adsorption technologies can be selected for reaching the mentioned goals, namely, the inter-seasonal heat storage and the regeneration of heat/moisture in dwelling ventilation systems. Both technologies have not reached yet a degree of perfection that is needed for successful commercialization. The appropriate units have to be more robust, compact and provide better heat and mass transfer, whereas the adsorbents must exhibit larger heat storage capacity and lower cost. To reach two above mentioned targets and make the adsorption technologies better competitive with more mature technologies, like PCM or sensible heat storage, further R&D is required in the field of adsorbents, heat and mass transfer, and advanced components.
We hope that this review will give new impulses to further consolidating international R&D activities in materials science and applied thermal engineering to obtain novel revolutionary adsorbents and technologies for improving energy efficiency and thermal comfort in buildings.
The author thanks the Russian Foundation for Basic Researches (project 14-08-01186a) for partial financial support.
UN-HABITAT (2008). State of the world’s cities report 2008–9: Harmonious cities: http://www.fastcodesign.com/1669244/by-2050-70-of-the-worlds-population-will-be-urban-is-that-a-goodthing (accessed November 13, 2015)
DECC (Department of Energy & Climate Change), Energy Consumption in the UK. Overall Energy Consumption Factsheet, Department of Energy & Climate Change, 2013, Available from https://www.gov.uk/government/publications/energy-consumption-in-the-uk (last accessed 13/11/15)
Abdellatif, M and Al-Shamma’a, A Review of sustainability in buildingsSustainable Cities and Society201514171177https://doi.org/10.1016/j.scs.2014.09.002
NRC (2006). Operating energy in buildings. Retrieved from http://cn-sbs.cssbi.ca/operating-energy-buildings (last access - 13/11/15)
Ziesing H-J, Schlomann B, Rohde C, Eichhammer W, Kleeberger H,Tzscheutschler P: (2011). Anwendungsbilanzen für die Endeniergiesek-toren in Deutschland im Jahr 2008. In AG Energiebilanzen beauftragt vom BMWiProjektnummer 40/08
Buildings Energy Efficiency in China, Germany, and the United States, Climate Policy Initiative, April 2013, http://climatepolicyinitiative.org/wp-content/uploads/2013/04/Buildings-Energy-Efficiency-in-China-Germany-and-the-United-States.pdf (last access 13/11/15)
Energy Efficiency Policies and Measures in Germany, ODYSSEE- MURE 2010, Monitoring of EU and national energy efficiency targets, Karlsruhe, November 2012, http://www.isi.fraunhofer.de/isi-wAssets/docs/x/de/publikationen/National-Report_Germany_November-2012.pdf (last access 13/11/15)
Report «Оn enhancement of energy efficiency of the Russian economy». Arkhangelsk, April 2009; http://www.cenef.ru/file/Report%2025.05.09.pdf (last access 13/11/15)
Bashmakov I, Borisov K, Dzedzichek M, Gritsevich I, Lunin A: Resource of energy efficiency in Russia: Scale, costs and benefits. 2008. Moscow: CENEf – Center for Energy Efficiency. Developed for the World Bank 102p. http://www.cenef.ru/file/Energybalances-final.pdf Accessed 13/11/15
Filippov, SP, Dil’man, MD and Ionov, MS The Optimum Levels of the Thermal Protection of Residential Buildings under Climatic Conditions of RussiaTherm Eng201360841851https://doi.org/10.1134/S0040601513110037
Ürge-Vorsatz, D and Novikova, A Potentials and costs of carbon dioxide mitigation in the world’s buildingsEnergy Policy200836642661https://doi.org/10.1016/j.enpol.2007.10.009
Riffat, SB, Zhao, X and Doherty, PS Application of sorption heat recovery systems in heating appliances - Feasibility studyAppl Therm Engn2006264655https://doi.org/10.1016/j.applthermaleng.2005.04.015
Zheng, X, Ge, TS and Wang, RZ Recent progress on desiccant materials for solid desiccant cooling systemsEnergy201474280294https://doi.org/10.1016/j.energy.2014.07.027
Mezentsev, YI IV and Mukhin, VA A new approach to regenerating heat and moisture in ventilation systemsEnergy and Buildings200840204208https://doi.org/10.1016/j.enbuild.2007.02.029
Mardiana-Idayu, A and Riffat, SB Review on heat recovery technologies for building applicationsRenew Sust Energ Rev20121612411255https://doi.org/10.1016/j.rser.2011.09.026
Yu, N, Wang, RZ and Wang, LW Sorption thermal storage for solar energyProg Energ Combust201339489514https://doi.org/10.1016/j.pecs.2013.05.004
N’Tsoukpoe, KE, Liu, H, Pierrès, N and Luo, L A review on long-term sorption solar energy storageRenew Sustain Energy Rev20091323852396https://doi.org/10.1016/j.rser.2009.05.008
Kuznik, F and Johannes, K A review of chemisorption heat storage in low energy buildingsEnergy Procedia20145723332341https://doi.org/10.1016/j.egypro.2014.10.241
Hauer, A Evaluation of adsorbent materials for heat pump and thermal energy storage applications in open systemsAdsorption200713399405https://doi.org/10.1007/s10450-007-9054-0
Xu, J, Wang, RZ and Li, Y A review of available technologies for seasonal thermal energy storageSol Energy2014103610638https://doi.org/10.1016/j.solener.2013.06.006
Aydin, D, Casey, SP and Riffat, S The latest advancements on thermochemical heat storage systemsRenew Sustain Energy Rev201541356367https://doi.org/10.1016/j.rser.2014.08.054
Casey, SP, Elvins, J, Riffat, SB and Robinson, A Salt impregnated desiccant matrices for ‘open’ thermochemical energy storage—Selection, synthesis and characterisation of candidate materialsEnergy and Buildings201484412425https://doi.org/10.1016/j.enbuild.2014.08.028
Raldow, WM and Wentworth, WE Chemical heat pumps - a basic thermodynamic analysisSol Energy1979237579https://doi.org/10.1016/0038-092X(79)90046-X
Close, D and Dunkle, R Adsorbent beds for energy-storage in drying of heating systemsSol Energy197719233238https://doi.org/10.1016/0038-092X(77)90066-4
Abedin, AH and Rosen, MA Closed and open thermochemical energy storage: Energy- and exergy-based comparisonsEnergy2012418392https://doi.org/10.1016/j.energy.2011.06.034
Michel, B, Mazet, N, Mauran, S, Stitou, D and Xu, J Thermochemical process for seasonal storage of solar energy: characterization and modeling of a high density reactive bedEnergy201247553563https://doi.org/10.1016/j.energy.2012.09.029
Aristov, YI, Restuccia, G, Tokarev, MM and Cacciola, G Selective water sorbents for multiple applications: 10. Energy storage abilityReact Kinet Catalysis Letters200069345353https://doi.org/10.1023/A:1005616420331
Frazzica, A, Sapienza, A and Freni, A Novel experimental methodology for the characterization of thermodynamic performance of advanced working pairs for adsorptive heat transformersAppl Therm Engn201472229236https://doi.org/10.1016/j.applthermaleng.2014.07.005
Aristov, YI, Tokarev, MM and Sharonov, VE Universal relation between the boundary temperatures of a basic cycle of sorption heat machinesChem Eng Sci20086329072912https://doi.org/10.1016/j.ces.2008.03.011
Aristov, YI Concept of adsorbent optimal for adsorptive cooling/heatingAppl Therm Engn201472166175https://doi.org/10.1016/j.applthermaleng.2014.04.077
Critoph, RE Performance limitation of adsorption cycles for solar coolingSol Energy1988412131https://doi.org/10.1016/0038-092X(88)90111-9
Saha, BB, Chakraborty, A, Koyama, S, Srinivasan, K, Ng, K, Kashiwagi, T and Dutta, P Thermodynamic formalism of minimum heat source temperature for driving advanced adsorption cooling deviceAppl Phys Lett200791111902https://doi.org/10.1063/1.2780117
Aristov, YI Challenging offers of material science for adsorption heat transformation: a reviewAppl Therm Engn20135016101618https://doi.org/10.1016/j.applthermaleng.2011.09.003
Aristov, YI Novel materials for adsorptive heat pumping and storage: screening and nanotailoring of sorption properties (review)J Chem Engn Japan20074012421251https://doi.org/10.1252/jcej.07WE228
Gordeeva, LG and Aristov, YI Composites “salt inside porous matrix” for adsorption heat transformation: a current state of the art and new trendsInt J Low Carbon Techn20127288302https://doi.org/10.1093/ijlct/cts050
Stach, H, Mugele, J, Jaenchen, J and Weiler, H Influence of cycle temperatures on the thermochemical heat storage densities in the systems water/microporous and water/ mesoporous adsorbentsAdsorption200511393404https://doi.org/10.1007/s10450-005-5405-x
Posern, K and Kaps, C Calorimetric studies of thermochemical heat storage materials based on mixtures of MgSO4 and MgCl2Thermochim Acta20105027376https://doi.org/10.1016/j.tca.2010.02.009
Casey, SP, Aydin, D, Riffat, SB and Elvins, J Salt impregnated desiccant matrices for ‘open’ thermochemical energy storage - Hygrothermal cyclic behaviour and energetic analysis by physical experimentationEnergy and Buildings201592128139https://doi.org/10.1016/j.enbuild.2015.01.048
Ristic, A, Zabukovec Logar, N, Henninger, SK and Kaucic, V The performance of small-pore micro-porous aluminophosphates in low-temperature solar energy storage: the structure–property relationshipAdv Funct Mater20122219521957https://doi.org/10.1002/adfm.201102734
Kakiuchi, H, Iwade, M, Shimooka, S, Ooshima, K, Yamazaki, M and Takewaki, T Water vapour adsorbent FAM-Z02 and its applicability to adsorption heat pumpKagaku Kogaku Ronbunshu200531273277https://doi.org/10.1252/kakoronbunshu.31.273
Jänchen, J, Ackermann, D and Weiler, E Calorimetric investigation on zeolites, AlPO4’s and CaCl2 impregnated attapulgite for thermochemical storage of heatThermochim Acta20054343741https://doi.org/10.1016/j.tca.2005.01.009
Shimooka, S, Ooshima, K, Hidaka, H, Takewaki, T, Kakiuchi, H, Kodama, A, Kubota, M and Matsuda, H The evaluation of direct cooling and heating desiccant device coated with FAMJ Chem Engn Jpn20074013301334https://doi.org/10.1252/jcej.07WE193
Li, G, Qian, S, Lee, H, Hwang, Y and Radermacher, R Experimental investigation of energy and exergy performance of short term adsorption heat storage for residential applicationEnergy201465675691https://doi.org/10.1016/j.energy.2013.12.017
Myat, A, Ng, K, Kyaw, T and Kim, Y-D Experimental investigation on the optimal performance of Zeolite–water adsorption chillerAppl Energy2013102582590https://doi.org/10.1016/j.apenergy.2012.08.005
Akiyama, G, Matsuda, R, Sato, H, Hori, A, Takata, M and Kitagawa, S Effect of functional groups in MIL-101 on water sorption behaviourMicroporous Mesoporous Materials20121578993https://doi.org/10.1016/j.micromeso.2012.01.015
Yaghi, OM, O’Keeffe, M, Ockwig, NV, Chae, HK, Eddaoudi, M and Kim, J Reticular synthesis and the design of New materialsNature2003423705714https://doi.org/10.1038/nature01650
Henninger, S, Habib, H and Janiak, C MOFs as adsorbents for Low temperature heating and cooling applicationsJ Am Chem Soc200913127762777https://doi.org/10.1021/ja808444z
Jeremias, F, Lozan, V, Henninger, SK and Janiak, C Programming MOFs for water sorption: aminofunctionalized MIL-125 and UiO-66 for heat transformation and heat storage applicationsDalton Trans2013421596715973https://doi.org/10.1039/c3dt51471d
Furukawa, H, Gándara, F, Zhang, Y-B, Jiang, J, Queen, WL, Hudson, MR and Yaghi, OM Water adsorption in porous metal − organic frameworks and related materialsJ Am Chem Soc201413643694381https://doi.org/10.1021/ja500330a
Deng, J, Wang, RZ and Han, GY A review of thermally activated cooling technologies for combined cooling, heating and power systemsProg Energ Combust201137172203https://doi.org/10.1016/j.pecs.2010.05.003
Liu, H, Nagano, K and Togawa, J A composite material made of mesoporous siliceous shale impregnated with lithium chloride for an open sorption thermal energy storage systemSol Energy2015111186200https://doi.org/10.1016/j.solener.2014.10.044
Zhu, D, Wu, H and Wang, S Experimental study on composite silica gel supported CaCl2 sorbent for low grade heat storageInt J Therm Sci200645804813https://doi.org/10.1016/j.ijthermalsci.2005.10.009
Wu, H, Wang, S and Zhu, D Effects of impregnating variables on dynamic sorption characteristics and storage properties of composite sorbent for solar heat storageSol Energy200781864871https://doi.org/10.1016/j.solener.2006.11.013
Wu, H, Wang, S and Zhu, D Numerical analysis and evaluation of an open-type thermal storage system using composite sorbentsInt J Heat Mass Transfer20095252625265https://doi.org/10.1016/j.ijheatmasstransfer.2009.05.0161176.80048
Sapienza, A, Glaznev, IS, Santamaria, S, Freni, A and Aristov, YI Adsorption chilling driven by low temperature heat: New adsorbent and cycle optimizationAppl Therm Eng201232141146https://doi.org/10.1016/j.applthermaleng.2011.09.014
Aristov, YI, Sapienza, A, Freni, A, Ovoschnikov, DS and Restuccia, G Reallocation of adsorption and desorption times for optimizing the cooling cycle parametersInt J Refrig201235525531https://doi.org/10.1016/j.ijrefrig.2010.07.019
Mitsubishi Plastics. Inc. AQSOA - Product Brochure: http://www.aaasaveenergy.com/products/001/temperature/ (last access 13/11/15)
Li, Q, Flamant, Q, Yuan, X, Neveu, P and Luo, L Compact heat exchangers: a review and future applications for a new generation of high temperature solar receiversRenew Sust Energy Rev20111548554875https://doi.org/10.1016/j.rser.2011.07.066
Amin, MR and Lindstrom, JD Transient thermal simulation of counter flow compact recuperator partition platesAppl Therm Engn2012481117https://doi.org/10.1016/j.applthermaleng.2012.04.030
Dallaire, J, Gosselin, L and Silva, A Conceptual optimization of a rotary heat exchanger with a porous coreInt J Therm Sci2010495462https://doi.org/10.1016/j.ijthermalsci.2009.07.027
Mert Cuce, P and Riffat, SB A comprehensive review of heat recovery systems for building applicationsRenew Sust Energy Rev201547665682https://doi.org/10.1016/j.rser.2015.03.087
Alonso, MJ, Liu, P, Mathisen, HM, Ge, G and Simonson, C Review of heat/energy recovery exchangers for use in ZEBs in cold climate countriesBuild Environ201584228237https://doi.org/10.1016/j.buildenv.2014.11.014
Zhang, L-Z Progress on heat and moisture recovery with membranes: from fundamentals to engineering applicationsEnergy Convers Manag201263173195https://doi.org/10.1016/j.enconman.2011.11.033
Zhang, L-Z, Zhang, XR, Miao, Q and Pei, L Selective permeation of moisture and VOCs through polymer membranes used in total heat exchangers for indoor air ventilationIndoor Air201222321330https://doi.org/10.1111/j.1600-0668.2011.00762.x
Kistler, KR and Cussler, EL Membrane modules for building ventilationChem Eng Res Des2002805364https://doi.org/10.1205/026387602753393367
Spengler, JD and Sexton, K Indoor air pollution: a public health perspectiveScience1983221917https://doi.org/10.1126/science.6857273
Nasr, MR, Fauchoux, M, Besant, RW and Simonson, CJ A review of frosting in air-to-air energy exchangersRenew Sust Energy Rev201430538554https://doi.org/10.1016/j.rser.2013.10.038
Meunier, F Adsorption heat powered heat pumpsAppl Therm Eng201361830836https://doi.org/10.1016/j.applthermaleng.2013.04.050
Ziegler, F Sorption heat pumping technologies: comparisons and challengesInt J Refrig200932566576https://doi.org/10.1016/j.ijrefrig.2009.03.007
Vasiliev, LL Heat pipes in modern heat exchangers (review)Appl Therm Eng200625119https://doi.org/10.1016/j.applthermaleng.2003.12.004
Wang, RZ Performance improvement of adsorption cooling by heat and mass recovery operationInt J Refrig200124602611https://doi.org/10.1016/S0140-7007(01)00004-4
Pons, M and Poyelle, F Adsorptive machines with advanced cycles for heat pumping or cooling applicationsInt J Refrig1999222738https://doi.org/10.1016/S0140-7007(97)00042-X
Aristov, YI, Girnik, IS and Glaznev, IS Optimization of adsorption dynamics in adsorptive chillers: loose grains configurationEnergy201246484492https://doi.org/10.1016/j.energy.2012.08.001
Ng, KS, Chua, HT, Chung, CY, Loke, CH, Kashiwaga, T, Akisawa, A and Saha, BB Experimental investigation of the silica gel - water adsorption isotherm characteristicsAppl Therm Engn20012116311642https://doi.org/10.1016/S1359-4311(01)00039-4
Dubinin, MM Adsorption equilibrium of water on NaX zeoliteColl Czech Chem Commun196631406414https://doi.org/10.1135/cccc19660406
Gorbach, A, Stegmaier, M and Eigenberger, G Measurement and modeling of water vapor adsorption on zeolite 4A - equilibria and kineticsAdsorption2004102946https://doi.org/10.1023/B:ADSO.0000024033.60103.ff
Aristov, YI, Tokarev, MM, Cacciola, G and Restuccia, G Selective water sorbents for multiple applications: 1. CaCl2 confined in mesopores of the silica gel: sorption propertiesReact Kinet Cat Lett199659325334https://doi.org/10.1007/BF02068130
Aristov, YI, Restuccia, G, Tokarev, MM, Buerger, H-D and Freni, A Selective water sorbents for multiple applications. 11. CaCl2 confined to expanded vermiculiteReact Kinet Cat Lett200071377384https://doi.org/10.1023/A:1010351815698
Goldsworthy, MJ Measurements of water vapour sorption isotherms for RD silica gel, AQSOA-Z01, AQSOA-Z02, AQSOA-Z05 and CECA zeolite 3AMicroporous Mesoporous Materials20141965967https://doi.org/10.1016/j.micromeso.2014.04.046
Glaznev, IS and Aristov, YI The effect of cycle boundary conditions and adsorbent grain size on the water sorption dynamics in adsorption chillersInt J Heat Mass Transfer20105318931898https://doi.org/10.1016/j.ijheatmasstransfer.2009.12.0691191.80001
Sapienza, A, Santamaria, S, Frazzica, A, Freni, A and Aristov, YI Dynamic study of adsorbers by a new gravimetric version of the large temperature jump methodAppl Energy201411312441251https://doi.org/10.1016/j.apenergy.2013.09.005